 all right got a freezer here fans ain't running defrost clock is fine that was a pack full of crap or the filter and it appears to be running but the fans ain't running you see all the water right there and it just came out of defrost not too horribly long ago so my thought is that i don't have enough refrigerant to bring the temperature down on the coil so the fans are coming on judging from it i'm just surprising this has never been tapped into it that's not warm at all now that's nice and cold so it's more than cold enough that it should be coming on but it's not so what i like to do is i'll put this in my pinch off tool to hold it so it doesn't twist in my hand and i'll use my spin switch to convert that into something that i can slide right over top of that stub tube so we'll pinch it down with this part here chop off the end brace that on re-round it and then we can check the suction pressure in that way if it's low we know that it's definitely low if it's not then we got a bad switch up above so we pinched it off cleaned it up chopped off the stub there slide this on we'll brace it on and we'll check that charge after we re-round it so we got that on there like that take this side down and re-round it kept the top core in there pinch it off just back together so no time for truth the pressures are a little low but it should be coming on so checking that out there white goes to red red when it closes goes to black and that should bring on the fans fans come on we should be good to go buy a lot to order another defrost termination switch fan delay switch it's a combo switch and it should work when the condenser is not hot like it was i mean granted the vapor is not running it kind of led me down that rabbit trail but we'll go and get that bypass get them running recheck the suction pressure and stuff when we get done and see how we're doing another issue you can have these as relays there can act up not bring the system on but obviously since the compressor is running that's not it oh there's our switch i'm going to go ahead and undo that bring it down a yank the fan motor fan blade off to get to it quickly all right just looking at it here you can see it's came out of a shell a little bit so that's definitely garbage so a scandy evaporator and i don't get nothing up there so it's probably in this line right here it all rotted out because it condensates this is really annoying as you know this is one of my newer detectors and it's been around forever so i'm going ahead and peeled it all off because i wanted to make sure before i called them it ain't gone off once now the pike name looks like hell of course the whole machine does too but i'm not getting anything so it makes you wonder okay if it was just the insulation then they should go off right there and it's not so i'm getting all up in that suction line and the where it got it from i really don't i guess i'll rescan the evaporator because i thought it was probably trailing down the suction line there and coming down in below so all right i just scanned it with the h10 there and even the ultrasonic and i didn't pick up anything all right just reuse some of those clips you have from those thermostats we replaced before so we got that and that it pushes back out of the way and they're protected with technically oem fittings so get the fan blade on there and see what we got okay we need new grills on this thing like pronto both of them are really bad so we're gonna order those i'm gonna tell them the motors are really slow it's starting up so they should get replaced also a lot cheaper to do it now than later somebody's gonna get their finger cotton out there and it's gonna take their finger workers comp ain't cheap make sure this clock is set for 30 minutes but i surely don't want it running a full 45 and it's set out