 All right, so we've got a walk-in freezer here. That's not working right It's always a great sign when you get here and the covers off of it They said the compressor is not running, which is very specific Hopefully it's just a maintenance guy took a peek So let's go up take our own peak and see what's going on. Well, no look too bad It's like they got a digital thermostat in there because you get a sensor bulb So let's see what we got going on here. All right, so I'm corrected here It's a walk-in cooler not the walk-in freezer Even though it's got a little package blower evaporator on top of the cooler where usually the compressors that this one here Has been remotely put over here so Compressor is not hot fan motor is not hot Curious George says push the button Button Curious George is wrong. It's not it. It looks like that goes to that one. You have 244 million volts across that thing Tight as tight can be there's a good chance that thermostat could possibly Be Causing the solenoid if it's got one which I think it does Set down Five ten fifteen fifteen pounds is where we're at So our solenoid must be not opening up. So what I'm gonna assume all right, so I'm not really sure how that's supposed to work with just two wires going to it So I'm assuming this don't work anymore Right, so it's not getting power to it You have to crawl up there and see if we get it there that junction box there. It's kind of A little tight on the ceiling here as you can see and literally not Really get into anything get that really go down through the ceiling to how to get to it Hey, so I got a hundred twenty four on the one you'll lead To ground this is neutral. I think like the ground. I've got a hundred twenty four To the neutral of whatever let's just assume it's a neutral 20 Have nothing crawl back over there White Wanted many black No, just one black wonder what that red wire there goes to it's practically pulled right out of the socket That does not look right you find the breaker for this thing so I can actually investigate it That don't do you no good does it? Let's say that might have something to do with it According to this It's your ACM foot Output common sense telling you that shouldn't You unplugged like that They stretched these wires so flipping tight You see it I know it's looks really new to which kind of sucks And it pulled out Yeah, that one's a little loose That one's loose So probably get that right. I'm gonna see if that does scan in That plastic and I don't even snap it That's the real finger control for giggles See what this comes up with My vice at the page sure. Let's do it. Okay. It looks like that's Normally open normally close and they put an L in front of it. I should be on the normally open I wonder if that came undone and fell over to it Now let's fix that that probably is not gonna help us none. Hey, I just heard it kick on So it must have worked Look at some of these other settings here. They got so I can kind of figure out what they are So they wanted off the 33 and on at 38 So they really much to set this thing I need to call our maintenance guy. I thought what how long we've had this because it's just something started or Lo and behold it's working Some pressures hold them pretty steady there Cooler 61 degrees and we're flashing We're gonna watch it run for a little bit. It just kicked on Let it run for a bit see how it goes may have to add a little to it Okay, so we've got her all set up to go I'm about 240 Head and we're still flashing pretty good down there Okay, so we added a little extra for the winter charge and pumping it down. We're gonna see where our receivers at Also gonna make sure this thing shuts off at a positive pressure And that it's able to do it. So we're kind of killing two birds at one stone here Good just staying in the happy zone Windier and snot up here So chances of finding it if it's outside here Slim to none, but I'm kind of curious if it ain't around this Pressure switch here. So we got Kind of oil on it All right twice I've gotten a little something out of this Trying to leave it on the cover. So I was trying to leave the cover on there So that maybe it would help accumulate it a little bit I mean our primary issue here Original reason for this calls because that loose wire fell out of the thermostat All right, so we warmed it up a touch You can see we're kind of cooler at the bottom there and all of a sudden boom it jumps up to 133 about Right in that ballpark there. So we should build out a little bit more to it Just to be safe Okay, so we added a little bit more to it You can see it's come up and right about there it starts to change Jumps up quite a bit in that area there so Somewhere between here and there is where we're at So it's a little over half 60 percent 70 percent somewhere in that ballpark. So we should be good there Now go ahead and scan the inside real quick Nice to see what I'm doing. I Have yet to figure out why they like to wire the flippin fans with the lights it's you know when I When I did my house, I actually Wired the outlets separate from the lights So if you wanted to do work on the outlets, you'd still have lights to work But for some reason now of all the stupid ass codes they come up with That's not one of their codes All right, you got to remember this thing here has been running And I shut it off so that it would trap some of the refrigerant in the coil, but for the most part This thing's only running at about 30 pounds pressure maybe something like that. So We don't have a lot of static pressure on this thing See if we can get to Sometimes it does better on the original normal mode, honestly built so eight up Everybody tries to get 600 years out of stuff They say it's at the top of the TXV's head Confident that it's not leaking We least with this amount of Mount of pressure on it. So Well, I'm gonna go ahead and just wrap this one up They want to go further with and do a full blown leak check. We can do that We could isolate it and then pump it up But that's gonna be a lot more money in time and generally the cost of refrigerants a whole lot cheaper Depending on how often they have to do it. Oh boy If you only had all the story sometimes So I talked to the maintenance guy and we bypassed this because we're having random shutoffs And that seemed like I just changed pitch So anyhow He just changed this thing on Monday And they were having problems before he changed that so now we have a new set of issues So we don't know if this was an issue So we it was already bypassed to try to eliminate it So now we've got this thing here, which like I said, they were having issues before they changed this So who knows this is great. I mean if you would have just been given this information in advance You would have looked for other things besides the obvious thing that you found But like I said, we found it low on charge and we looked things over and it's about all you can do for right now And it does sound like this fans change pitch Hard to say We're 37 degrees and dropping We're gonna leave this bypass. He's gonna re hook it up if If he doesn't have any issues and then see if that X up after he hooks it So if you guys like the video and you want to see more like it Make sure you subscribe give it a thumbs up and don't predict click that notification bell till next time guys We will catch you on the next one