 and running this last call for someone else that would have been stuck with it so this place is usually a real treat so I'm sure you guys might have an excellent video to watch so let's go see what kind of mess I get into so anyhow as you see things aren't looking so good ice cream soft it's it's got the wiggle wiggle but this old bird it was originally 502 you about guarantee that here but I'm hoping that the compressor has poe oil in it for a force probably it's going to go back in there and see we've got major issues I've been here on plenty of calls in the past it just needs a lot of work move this earlier to show it to the owner but all right there's what happened it broke loose that is the looks like the oil pressure switch you can see all the oil down here it'll keep that kind of crap from happening so we got an oil pressure switch here I'm not going to try to fix it I thought about it it's just not worth it I normally wouldn't do it and there's no reason to go that route so we've got that and a couple more of them back here if we need them I'll just get us to there and we got the orange goblin right there you know what good grief I still need a look I need to make sure that txv head I think it could be 22 it could have been 502 I'm not even thinking today yep 404 502 the coil is clean that's not I've got that I wanted to make sure man that would suck it could always be 22 especially when it's this freaking old you can't take anything for granite man it will bite you in the pooper hole I'm on this labeling kick so I bought me a labeler and all kinds of different labels bought the wrap arounds bought the you know all the different things but when we get that on there we're going to know what the heck you're actually working on that way no more guessing we'll uh get that put on there and let's get this thing emptied out of the oil that's in there now showed how to do this before what we'll end up doing is we'll slightly pressurize it and we'll push that oil right out and then we'll put in the poe you know what looks like somebody actually but 404 in there and that's what's been working we may not need to mess with the oil but the oil looks like it's a little low I mean I have to do that conversion maybe I'll just add to it which I'm shaking it right there buddy it it blew it all out it blew almost all of it out did okay on that lovely were you just feeding something else who knows 96 was when that was built we get her back up there this uh pressure switch would have shut it down when it lost its charge so there's still refrigerant I'm sure vapor and this filter dryer this is one of those jobs where you're keeping cost as low as possible got our oil levels back up somebody changed it at one point in time I mean for us or whoever ended up doing it switched it to 404 would have had to put the poe oil in there they would have probably lost the compressor by now I'd like to see that even with a tube on it this will have a tube when I get done I should be able to just copy everything right over from one to the other looks like the same machine to me so this one here must have broke off at one time went ahead and put one on that switch there just in case I don't want to have to come back and do this again later we did everything but the loop I don't want to spend a bunch of time on it but I'm going to do a wire tie on that part there and do the same thing for this other one wire ties on those loops that'll help keep them from shaking get this thing evacuated really do you hear that green indicator still green this obviously has vapor in it it didn't go into a negative the low pressure switch cut out we're doing this on a budget we're well over a thousand dollars as it is so we're just gonna do what we gotta do to get it going and get them back up and going as quick as possible Friday night and you know don't help with the freezer down so you guys know me better than that but we're doing a down and dirty evacuation on this that is not where you took your gauge at you guys just see me do it a million times but they figured it out yet like I said changing what I want may have to do it again but we're going to be valving off and then we'll change the hoses and go back to the manifold we'll dump it in all right but things in perspective for you guys I valve this thing off to isolate the vacuum pump when I did that my vacuum went up it actually should have went down because you was pulling on just the hoses that's how bad these king valves and stuff are actually leaking this system's known for leaking it needs replaced I mean if you didn't notice that on the inside isn't very bad shape so what I did is I bled everything up to the service valves through the manifold opened up the liquid valve there and we're dumping in liquid straight into the receiver which were five pounds so far we're going to empty this one completely in there because I know there's not a whole lot in there but we're sucking that in and once we do that we'll go ahead and then kick it on and then we'll get it charged up the rest of the way we got away from the fans come on there's all kinds of things that's going to happen yet I mean this thing is old when you can stick your hands through the grill like that and grab a hold of the fan you're you're old that's back when safety wasn't that big of a deal so far six pounds area it seems like I thought we're just going to die out of we dumped them with seven pounds in and another 11 pounds we're about 18 area we'll watch her just kick on turn the build the head up you gotta watch that once that fan kicks on everything's going to change on us I'm sure staying down at lower third level there isn't on yet so things are going to change quite a bit once those come on it's uh still let this thing go for a while running uh 15 with 190 head so it's built enough we're gonna spray those fittings you can see how we got some shake going on there I like to put my loop down closer to the device that way you don't have as much weight up in the air causing it to shake more to me it just makes more sense so we're gonna lower that loop down to there that'll get rid of some of the shake and it won't be as bad so see how it ain't shaking as bad now we have no shake at all here on that line no shake on that line there pretty good on that there so 18 pound suction so yeah we'll go back in double check that I'm sure it will flash off you just can't really do much until it gets its thing uh optimal conditions but it's fairly tired a lot of the noise is just that fan sticking the crap out of it nothing's driving nuts it's like a compressor with replacing 20 just dropping because that fan's not running yet so the fans are running we're in to double check that so we are running there we have full cyclist just there on the stem that's great now it may go away when we close it now we got 14 pounds there all right so we bound it off waiting for it to pump down we'll make sure the thing shuts off we'll see where that level is in these off receivers we got underneath here you got the neighbor there a lot over there so really good size see where this thing shuts off fast I would think now would be good it's at one pound actually shuts off all right good so let's see what we got for receiver level all right guys so we went through we're finished up getting some wire ties on a few of the miscellaneous ones we sprayed all the flare fittings and sure we didn't have any leaks got our cap back on everything's good to go you know it's just uh one of the things that happen to this thing to get all the vibrate things break you can put these uh split quarter inch uh plastic tubes on there that helps out quite a bit um went ahead and labeled it put 21 pounds 404 in there we know that it's for uh peo e oil so I didn't see that there so all the same it's made it a little more obvious so the defrost box got a little bit longer to go before it's gonna hit for probably about three hours uh so we should be fine I'm gonna leave it behind for the time it took me to repair it the uh system's up and running we got full psyched last I'm pretty confident we're good on our levels that's about what I've seen before on these uh old units all right guys so we just came back in here it definitely feels like it's working the ice is starting to slush up on the ground from where things have fell down here before so it's a working uh you can see it's definitely freezing things so good enough for today