Rating is available when the video has been rented.
This feature is not available right now. Please try again later.
Published on Sep 16, 2012
Pump down on two condensing units as the equipment has been sold.
Found the right hand unit to have a poorly pumping compressor which is likely due to bad suction valves. The system dates from the mid 90's so has run a lot of hours, though i suspect poor installation and maintenance practices in its early life are factors in the failure.