 Well, it is windy up here. Yep, I'm here to kick on kick off. So we must have a leak of some sort Yeah, she's pretty low That's pretty up there what I'm seeing and they just need a new evaporator this thing is This video is brought to you in part by TrueTech tools quality tools essential support All right, so we got to say walk-in freezer. That's supposedly not working right Let's go take a peek see what we got Yeah, it's nice Astor-built Looks like it's just reading 10 Let's see what's going on supposedly it's 404 a what I'm seeing there Let's probably go up on the roof and see if we've got a solid cyclist. I Have not been to this location yet, but it's got the same Sensors and all that even though it's master built. I don't know if I'm assuming it's probably similar to a beacon system Let's go up on the roof. You gotta figure out where that's at. So there it is Wait, it's windy up here. Yep. I'm here to kick on to kick off. So we must have a leak of some sort That ain't good short cycle, baby. Well You can tell this is our freezer because it has the liquid injection there See if this one's the one that shuts down probably get down there here is a cyclist. Yeah, she's pretty low Yep, she's pretty low and that's what it's doing. It's going to pump in that oil right out of it Yeah, that's it And we put them both on the same Laint that about ignorant. Why would you put them both on the same disconnect? That's That is absolutely asinine. Look at all the cleaner that they've gotten into the fan blades there Around the motors they've lost because they got cleaner in it like that Well, we're gonna start looking for a leak. Obviously, it's got one somewhere somebody said something about possibly it's rather big I'm going to guesstimate that this Find piece of machinery here has Two loops in one coil. Do we have any oil out here? Don't see any oil It's super windy today, so it's up here on the roof may not be able to Find it. I got my ultrasonic. We'll try that I guess that's It takes I guess All right, let's see if we get a hit when we go on the door here You would think That would go off as we go in this room Nice We'll kind of give this thing an old lucky look and see what we can find here on it It would be nice if it's down here in one of the fittings around the end of the coil But we'll scan it over and oh go Yeah, lucky there That's not good is it? Well, let's see what it kind of parts per million it comes in because that'll tell me whether It's just a itty-bitty one or if it's a big one Yeah, that ain't good All right, you ready for this? Going right up there in that corner Which is going to be closest to your TXV and all that 500-600-7 We're just leaving it there for minutes where it stops and then we'll pull back and see if it comes up or down as I get closer to myself That's pretty up there Come my way a little bit It's getting higher. That's not good much higher Come a little bit more. Hey boy, that's really high. That's that's a pretty bad leak Come back in for another bite Unless it's leaking on that end. Hopefully it's leaking on the end and we can just fix that real quick We're in the 700s here So it's going down as I get closer to me Well, let this cover off. Maybe it was starting to dissipate now And now we're near the vicinity of what we have before I'm gonna grab my torch warm that up and we'll spray it I downloaded the manual at least it looks like the manual Said to hold PB1 which this one just says switch one. So we held it for the five seconds It says PD for probably pumped down And we're hoping that it's going to go into the defrost This does have electric defrost the one this one here is talking about has a reversing valve. I Could not get anything to bubble even when I warmed it up some but since we've got wires in there I don't want to get too crazy with the torch So I'm just gonna see if I can get it to go into a defrost and then that'll warm it up That'll also make it easier to fire a leak. It did work It pumped down it shot the fans and it just said DF which would be defrost Kind of interesting how they bring it all the way over to here nice and far over to this area We're okay and belt all this nastiness out. Which more of them did it like that now? unfortunately I'm not getting any hits because obviously it pumped down. That's the only downside now What I did do is pulled the evaporator sensor out Which is how it's going to determine when to shut down out of the coil that way it doesn't shut off I'm assuming probably 45 to 55 degrees so it'll get that coil nice and warm once it eventually gets out of defrost I'm gonna go up there and kill power to it and allow the refrigerant to come back down and then we'll go through and see if we Can scan it again because like right now It's probably got less than a pound or two pressure on it And now I'm not getting dilly squat. You can see the heat going across the ceiling there 19 is technically what this sensor Here is I think we're just about pretty well done with this thing. I'm gonna stick it back in there And that way it'll shut off and then we can kill power to it and that way we can get some pressure in here to Have a trigger I believe it was right there What's it reading on it? Yeah, look at that. She's zooming right on up there 40 And she should release here in a second 65 be the highest I would have figured Should hear the little expansion valve open up because that's your solenoid It's gonna have a drip time now a couple minutes to potentially five and just released We should start picking something up here real quick Yep, we're already getting stuff. There we go All right, let's go shut that off and then we might go spray it before it gets too cold Turn it back on went upstairs listen to it flow and I've sprayed it down I might have seen a little something around one of the Metal to the elbow, but not to the extent that it should be as strong as what it is I believe it's in the coil and if it's in the coil I'm not digging in there and what I'm seeing and they just need a new evaporator. This thing is pretty well I bet you this is original one and I think the store's been here for a long time I've completely drenched this thing with soap and It's I ran it underneath the water because to get it warmed up because it was for freezing in the spigot of my sprayer But I've got all of the joints and the outward back corners all the way in the Every little square inch of everything I can get that I would be able to fix up here was one of the stronger ones I think it might be potentially on the other side, but it's not where I'm at and to dig in there I don't see the point. It's just time to replace it All right, so depending on where I'm at You go in an inch or two into the coil and it gets tall or it gets higher They're getting higher and higher. So it's not just right at the very edge They're getting higher So the PPM works really good like here I am going closer to the outside where you would think it'd be easy to fix and went lower. That's good enough for me I'm not gonna tear the whole coil apart trying to fix it It's time to buy a new one. I'm gonna give them a call and see what they want me to do They don't really have a lot of options other than bringing a semi to unload it all. Otherwise, that's where we're at I just got done scanning all around up in here Around the face of the coil in the fan blades here Getting off that. I mean it is super super windy out here, but I wanted to protect myself Against the catastrophic leak that'd be out here that I don't know about And I'm getting nothing so at this point I got to call them and tell them what's going on See what they want to do. Like I said, they're probably gonna just juice it up, but I don't know how long it's gonna last That's pretty strong signal. They gave me the okay to go ahead and recharge it They're going to talk to whoever and then decide if they want to Have us replace it or whatever. So at this point, that's where we're at We're gonna go ahead and get it running. There's really a whole lot of options You got food on the line and that's just what we got to do We'll go ahead and go on our charging skill here, which is awesome. So convenient to not have to use your phone if you don't want to Get down here and go for your charging manual Should find it here in a second as soon as it gets the green. There's the C560 472 there it is. It completely connected. We'll zero that churned out There we go Man, I'll tell you what these 557s. I have been really really really happy with them I was not as happy with my 550s, my old ones. These ones here really early have been good I've been really happy with them. Of course my first 557s awesome. We're really good too. I mean, they lasted quite a while Yeah, it's already kicking out. I hate that I don't charge too fast, but aren't it not gonna have to So you don't keep much force like but the refrigeration is just gonna be there anyhow Yeah, geez I can't believe it doesn't have any type of timer to shut it down once it triggers Probably did back in the day But it doesn't anymore it wouldn't surprise me Yeah, that's like last summer. It's completely empty They're a little something. I don't see a headmaster on this at all That's kind of crazy Well, they must be able to do that with electronic TXP pretty much the same as the bone riser does Starting to fill it pretty quick actually I'm pretty surprised Apparently we're done put it in awfully fast. I mean that's way faster than I normally would do it, but I Feel like what's the point of setting our short cycling it over and over? I mean, there's definitely a lot of things this thing could use and I told him I said the compressor is an 06 on it That one there looks like that was changed an 09 I Bet you the equipment is a lot older than that. What do we got here? See if we can make it out on the serial number 97 is about what I bet you this thing was built About that. Yeah, I think it was about 97 or they did this Right about the eight and a half part. We finally hit solid I'm gonna go ahead and try out about a two extra pounds about a half something like that Then we'll wait see where we're at The other one wasted stay in full That's your cooler and they don't look horrible shave it. I mean, it's just How long until the coils start leaking up here? Freezers already at five I Seal is going out. I think it's better in the door doesn't have a seal then the door doesn't shut All right, what do we got three degrees there? All the fans running everything's picked back up We're good to go there. Oh good thing. I came back because I would have forgotten my acutrack Which I don't have the battery for That's gonna check it with that That would have probably done good, but either way it's it's done You know, there's just nothing more you can do it I gave it everything I got to try to make sure it verified what the leak was at and Just not seeing Any way to fix it without completely destroying the coil and you know right now it's 530 So I mean I stayed a lot later than normal trying to get them going so he did what he can do Anyhow till next time everybody catch you on the next one later