Rating is available when the video has been rented.
This feature is not available right now. Please try again later.
Published on Jan 8, 2011
This is a followup video to our original Generator Test Run video showing what happens on the UPS side when the main transfer switch moves from utility to generator power. The UPS is an Eaton 9355 30kVA N+1 redundant/scalable up to 4 units at 90kVA.