Rating is available when the video has been rented.
This feature is not available right now. Please try again later.
Published on Apr 11, 2012
Diagnosing Honda EM 5000 SX Generator with no voltage output. The rotor is bad in this generator, it took some time to figure that out. The Fix for this generator was: apply 12 volts to the rotor to start the loop, slowly load the generator down with more and more equipment starting with one 100 watt light bulb until the generator would self support the load. Once the generator was able to support 1000 Watts it worked as it should Basically the generator required a HARD CORE flashing of the field. Generators need to be started and used every quarter minimum if they are expected to work when needed.