 This is Nate Adams with energy smart home performance and I want to walk you through the habitat project now that the duct work is mostly in So here's what we're looking at This is put up for where the thermostat will go. That's pretty central in the house You can see there's a front door And over here and then it's going to have a central return Coming through there and then each bedroom as you return one there One over here purposely place some place where it's not super likely. They'll have furniture. So hopefully they don't get blocked and then The supply trunk we ended up running up into the attic. So this is coming from the crawl space below and Then up high You can see it pops up up here and there are two supplies that go over to the living room One there and one there and we're going to direct these up against the ceiling so the air goes up And over and mixes nicely so that hopefully nobody will ever feel the flow coming across them and Then I'm going to do ceiling diffusers here that go several different directions But the bed is going to be for instance that way and we're not going to send airflow that direction So hopefully we don't make anybody cold if there happens to be cool air blowing So that's one of them and the other bedroom Yeah, you know drywall walk through the wall still the other bedroom comes out over here and then from this main trunk line There'll be another one punched over that's going to go into the bathroom Somewhere up in here. I let them decide which one they want to do And then The last thing to note is they've done a pretty nice job of sealing the joints. So this is mastic right here It's also uses a tile glue It's not quite as thick as I'd like so the rule of thumb is thick as a nickel or nickel thick and That's not quite there and there's one joint if you can see right up in there that Definitely didn't get hit that we're going to need to try and figure out. This is where it gets tricky though because we're Stuck with some wood along there. So it's difficult to get these last couple of spots, but those spots are Well that one in particular looks quite leaky. That's a big gap So we'll get that adjusted when they come back, but certainly I'm happy with what I see thus far and Thanks to having this nice little attic space here It's a great place to run ductwork through the attic normally running ductwork through the attic is not the best idea in the world But in this case it's going to work just fine. It's actually really a convenient place to do it