 This video is brought to you in part by TrueTech Tools quality tools essential support Nobody talks to nobody most of the time Probably if it's never explained to the next person what's been going on then we got a case. It's leaking water And the stores too cold, so we're gonna just that yet All right guys, so we've got us a little cooler here that's got two condensers and Two evaporators got one down here Got a pan here You got a pan here on the other side What's going on is it's not regulating temperature very well? And we're trying to figure out is it a refrigeration issue See that one unit there. It's not running which I hit the high pressure switch to see if it shut it off My satisfied so Right now we're checking out thermostats if it's just a thermostat issue or what so we've got an evaporator fan there That's working just fine. We're gonna check this one here. Make sure it's working and a dig All this stuff out Get in there and get into it Want to make sure the obvious stuff's taken care of first And is running Which is always a good thing Both condensers feel warm like they're working the way they should I believe it's just a thermostat issue but wasn't sure if it was a Traditional thermostat that they used to regulate the temp Or if they were using a pressure control And they are using a temperature control Which is good Then we got a deep lost clock off so because of that So this is like I said not on a rack or anything Let's get in here and see if we can find out where this thermostat bulb is at There's TXV so the thermostat Is in the discharge line, which is fine if you compensate for it but unfortunately They've got it set for 40 degrees here That's not going to cut it Um I doubt it's just been dinked with I'd rather see it in the return path So we're going to move that but I think what we're going to do is go ahead and replace it either way because It should always be the same problem. It should never hit temperature and So you've got thermostats control in the contactor Which then controls the other stuff That looks like an awful lightweight wire there That's Kind of scary There's no way that's feeding all that stuff. So you've got power coming in here Interesting. Let's see what the ampereal is on that 8.5 8.9 you got up here on this 8.3 So surprisingly That seems a little Little off Got 11 there. So they're not completely 8.7 there Yeah, that's some haphazard looking wiring. I'll tell you that this All it's kind of scary the way they did it Amps there And it looped it from here to there and do the same thing on the black Not sure how they're breaking that don't make sense. Yeah, I just don't like that at all All right, so we killed the power Power comes in at the top or 208. I've gotten like a turn and a half or more out of this breaker And I did out of this side here too Go ahead and finish tighten up some of this stuff here. So we're going to do is we're going to go and change the thermostat We're going to set it for about 10 degrees area below what they wanted that. So if they're wanting to say 35 We'll set it for 25. They're wanting 37. We'll set it for 27 That way we don't freeze the product Had a double check on that. I knew we'd do that on our On the rack stuff, but I wasn't sure we was doing that on this little stuff But we are so we're going to go ahead and do that real quick we'll just Make that bolt out of there and get her in place I have a feeling what this happened because 40 degrees is really a high number I think they've been trying to adjust it and it's just probably not been getting the work done and they've just Set a higher and higher and now it's causing issues and nobody talks to nobody most of the time so Probably it was never explained to the next person what's been going on And then we got a case that's leaking water And the store's too cold. So we're gonna adjust that yet So I'll just swap this thing out piece for piece and run the wire up and across and over to the top Which it goes right up through the hole and Should be good to get. Can't get the other one out Pull this one in I'll just stick it in there What do you think? Got to get up and out a little bit further to be a little better There's not a real great way to Get up in there probably tears the evaporator coil So if you think about it Your temperature is always 10 or 15 degrees, but on how it's built You should have The temperature coming in to the coil would have to be lower as well But if this is laying up against one of these that would really throw it off So, yeah Maybe great if it get a little further up in there That would work probably a little bit better But That's where it's gonna go I'll see if I can get a little higher, but I don't think I can All right, so he's able to pull this back Get that wire or the uh Up into There that way it's not right beside the coil And uh, that should help get a more even temperature The brown stuff you're seeing sesame seeds Some of its breads and then it's not mouse Droppings or anything like that It's just uh, like I said from the bread Hopefully it'll work a little bit better I'll get this back in there seal this back up Some old silicone This keeps that air as it gets shoved up through there Falls out gets pulled back to here. We've got her mounted up Which I see I made a mistake here. Let me fix that real quick All right, so let's get this set up about right, which I think we are 10 15-ish There you go And flip this on and let's Turn that up so that don't click. Let's see or Seems like it's clicking on and off about 55 It's fighting off too much Okay, turn it down Turn it on did chop that wire off and restrict it underneath there set this thing for 20 Seven area great about the middle ish Let it run. I'm gonna go here and work on this other Project tightened all these connections up in here Check the contact here took the cover off. We ain't gonna have any bugs in here. It's gonna get in it So you can see there's a little part there about temperature change it But let's go ahead and run it and see if we have any issues see if it shuts off the right temperature Could always switch it to the other unused contact point there that they didn't use Make use of that. I think I'll do that when I come back over here All right, so we got the new condensate pan heater in there Put the meter on it Put it on max hold and it pulls seven amps. So that's working Let's go ahead and look this thing run. We'll get it back together and then Come back and check and I forget some of this other stuff done What we've got now is this one side gets about five degrees colder than the other check refrigerant pressures, which Hard as heck to get into that that we got into it with the probe instead of the gauges these hoses I've had nothing to problems with and so For adjusting the txv we were almost 16 degrees super heat on it So we're gonna try to get that down maybe around nine eight area And uh starting to let more refrigerant through on this coil now Super heat still only at 14 on this thing. It's very very slow But my hope is once we get this thing balanced out and putting out the cooling that it should It should be at about the same speed as the other Between that the thermostat and getting it a little bit better in the path there Should do a little bit better job All right, so we had to clear off this bottom shelf Which they'd love to put all these little things in there to make it more decorative So you gotta move all that out Get down here in the strain pan. You can see we got a little bit filled up there in the drain along with the pan also If you look at your air band It's just a little dirty so If your air Can't get pulled back into the fan down here. We'll be pulled in and push back up through the back of it And it comes back down. So we've got to run the sweeper on that because Kind of packed full of cred. There's a pump in here somewhere. And usually It's right there in that little spot right here. So See if we can dig into that. There's a screw in there Take the screw out All of us out Doesn't get the water. It's not gonna pump it up to the top So it pumps the water up to the top into a little heater pan up here Which Is right here And it just boils it away. There's this big old 1500 watt elements Everything's just a little bit tired Just a little bit All right, you got the old shop back at the old filter pulled out As you can see there's not really that much water in that pump So it appears most of it's right there. So I'm gonna Put the vacuum cleaner on that drain hole right there. That's all nasty and funky junkied See if we can pull that right through See what we get here Oh forgot to put a battery in it That was great. Wait the rest of that crud out of there here in a second Tough right, dude. Kick on here in a second. Let's make sure it pumps up to the top. We don't leak out of the top Yep, it pumped it up here, which is probably more than what it can handle, which is awesome Wonderful that's gonna be overfill here in a second Okay, so he's able to pull some of that out made a little bit of a mess Should have known that was gonna happen We'll check that cycle ass back here. See how that's doing. I'm sure it's probably flashing See if this water's getting warm Heat our element don't feel yeah, it's hot. Okay So we know that's working. That's good. I think this is how I'm dump the water out Can you believe I actually wanted to do this? All right, so we get this last bit of gunk out of here Let's see if the rest of this crud out go on to the heating issue they got All right, so we got that all cleaned up Everything back together We swept up the floor All I got to do is put those rags away and we should be good to go on this part Maybe we can get their heat adjusted I'm not sure it's not on the controller. I don't believe so probably up on the brook and a thermostat on a The duck somewhere is what I'm guessing All right, so we've got stat here With a remote sensor That's a duck heater And then The rest of them are all on the roof with the duck with the stats in the duck work So this one here is on cool still which we're just coming out of it. So it's running I've seen any flutters of flames. Look it over real good. Make sure it's safe and you'll get the other ones All right, so we got that one Okay So now all we got to do is get those two That one there Those then there a few of the others All right, so you can hear the belts loose Got it set on heat. It's nicely attached there That's the old control system. It don't work anymore It was elaborate at one time so Six more to go I think A little bit loose you can hear the squeaky squeak going on and I think it's not straight probably Yeah, well tighten her up just don't feel too bad there didn't get crazy and overtaken it See if we get a squawk. Let's go That's to do and I thought you'd like a monkey. Why is the fan not coming on immediately? Fan shouldn't have ran nonstop Now check the fan make sure it's on fan all the time. You can't remember I think I think carrier does shut off the fan when it goes into Heat mode we don't really do much of any Preventative maintenance, so they just call when things break. Come on. Let's go. Come on. Come on That's a little less squeaky all right This one was loose as a goose Swapped out one used belt for another used belt So that'll be better I did a video on this one once before So you can see the suction line there Little ice on it wait till you see the evaporator. She's a leaker. I've completely gone through this and cleaned it you can see Through they're pretty good. So we're gonna have to melt this baby down. Check this out So you take a look at it. She's a little rough I was good and just turn that off Look at this baby I can't even get my phone back behind here So we've got a a little birthing Pain here Say the least so, yeah Just a couple problems. It just happened. It was it was fine yesterday Okay No Yeah, we're gonna It's gonna take a little while I don't know if our I think we're low on charge is our biggest issue clocking here at running It's set for a 60 minute defrost. There's no reason why three of them for an hour would not keep that thing clean So i'm gonna try to knock off what I can knock off and then uh melt the rest About the only thing you can do This ought to make a difference It'll make it a little easier So if we can just Oh good grief Come at it from here And make it pop off the back or not Like that And then we'll work the backside a little more gently He scores Doing a row So, yeah Normally I would not probably do this if it was a new one But sometimes you gotta do what you didn't gotta do And he's worried about A few of his things getting spoiled so We'll get her get her He's got that little piece there left to go And then we'll Try to do the rest with water. You don't want to get rough like that on the coils Yeah, she's looking rough Yeah I'd say that's a little plugged up Just a little That may not have helped it a lot Could just been storing the water in the bottom of the pan, but I will know here once we get her clean Well, we're making progress Got the backside completely Yeah, never mind that Got it cleaned up. It was pretty bad on the back Got a lot of gunk out as you can see Yeah, he said go ahead and get the floor wet. They'll clean it up. So sounds good to me Got the fan bleeds out and gotta finish getting that rest that gunk out I think I switched that to 134a a while back. It was a year ago. Maybe I forget It's got a leak As you can tell it's Just um, it's not getting replaced. So we're going to go ahead and get that melted out of there Got the handy dandy Sprayer here. Thank goodness for that because I mean it really Helps give you a control got them washed off along with this here. They had nasty stuff all over it Reinstalled that out and got it all cleaned up looks a lot better than what it did I only have so much polish to go around Uh, I gotta blow these motors out with my blower yet. They got water all in them, but As long as you ain't using chemicals, I haven't had too many motors go out from just water Usually it's dry them off. You're good to go Not idea, but you know, there's not a whole lot you can do and it's impacted into the ice Did check make sure the thermostat that looks like it's about ready to go On a vacation uh, that it's uh Set on 35 area. See if we can get this turned on without getting shocked There we go That's always a good sign There's sparks So Let's go outside and See if we can reduce this. I'm assuming that's what's probably what's wrong clock does seem to be working. I did push it in Past the next defrost, which is just about ready to happen. So let's go outside All right, so we've got our drain hooked back up suction on I'm not gonna full with the High side just yet Think we'll be fine About guarantee what we're gonna find out is it's just Really really super low fans not running We'll scan it for leaks when we get done At this point, it's uh gotta run Definitely looking empty there Yeah, they've got problems. They know they've got problems. Just unfortunately it's not been handled So go ahead and juice the juicy juice the goose. So we've scanned Everything up here. Nothing in any of the controls. It's so windy out here. I mean, it's ridiculous. You can see The water driplet coming across I mean, it's it's it's just there's no way you're gonna pick anything up out here I got nothing on the inside So once again, it went low like it did a year ago or so about a pound and a half to almost two so it's uh It's beyond needing replaced But at this point I can't find it. It's way Way too windy out here Uh, it's got a lot of flare fittings on it. It could very easily be on one of those It could be on one of the controls, but I'm not picking anything up. So it's back up and running I'm gonna head on to the next one