 All right, so we got one here that basically last night. It wasn't wanting to run and Somebody made some adjustments on the stat and it started working and So now It's not working again. It's calling for cooling down on the thermostat. It's warm So that condenser motor is hotter and heck That might be our issue Yeah, real easy called So let's take a peek here get her opened up Look at that that big old fat hog right there 2011 contact was done in 13 so I Dollar disconnect on this one All right, so Now right there's one of our issues Where in the world that was it died? Left a leftover transformer in here. It's always nice so Let's give that family to spin just in case It's good for another 30 years It'll be fine Yeah, this will be one of the easy calls nothing exciting so we think You know what'll happen It'll be low on refrigerant compressors blown up something will be wrong. This little pig is a 60 by 5 at 370 and That compressor. I don't know if we can even tell what the heck it requires Kind of curious if it's the correct one because it was replaced once before This has worked for Nine years with that capacitor, so in reality, this is probably stupid, but Figure, we'll just go ahead and check it anyway You know the 1% solution here, so it's a Bristol I don't have an app for them and they're out of business Not happening Mazda go ahead and give it a little luck to see over at the filters filters look fine economizers unhooked Okay, so we're good there No problems here. We had a build a capacitor here got a 45 by 5 and a 15 so it comes out to 60 contactor actually You know contact or we're gonna change that to so we got the new contactor in there It's all wired up. It's got the bug shield on it We're gonna go ahead and turn this thing back on see if it runs check this belt real quick Don't look so. Okay No major issues there. They got her all back together. Let's go here and check this charge out Cold we're good Checking our super heat This is an orifice system not a TXV. So we're gonna check that Coil is a little bit dirty on that second piece. I mean just a little bit Super heats way too low, so it's overcharged. Coil is probably dirty Quite a bit of heat load down there. We should have a higher suction. Now that sub cooling is not accurate Tell a little something about what's going on here check sub cooling. All right taking a look here at the evaporator So we may have some duct work issues, which would not surprise me sub cooling's up there on 25 Which kind of confirms the coil is a little dirty gained a little heat here with the cover off, so we're sucking the outside air in Super heats up to around 18. So she's starting to stabilize Go ahead and close this back down see what it does kind of That's some good draw on it See whether or not it drops back down Just that heat load change right there look at the suction already dropping Here's to me. We don't have enough airflow. So like I said 60-pound suction pretty much jack squat for super heat Pull in a little outside air The heat load comes in and super heats gonna jump up the stairs and look and see if we got some return airs That are blocked off or whatever the case But everything looks good once we get some real real return air going on now. We could mimic a Maybe a 10 inch return there See how that does still There's some massive air there Not a reality. I mean it should be pulling some outside air in but it's all unbooked minimum positioning is gone Almost instantaneously comes right back up. So got to go downstairs take a look what sucks is it's been like this for how many years It's got one Oh, that's why it's not working right I Can't do that. This is guys telling me that they blocked it off, but I'm looking at the return here. It looks fine, but they have a filter in there. It's kind of dirty There you go goes on over that away There's your supplies quite a distance away. So we're wide open there You can see it's all up in there It's like there's a duck sensor right here Here's what we got Got a high efficiency filter in there and these things hardly ever changed. I don't know if they Yeah, somebody built that. It's kind of ingenious But yeah, this is this is in the freaking ceiling grid Some of you younger guys may not have seen these they may not be popular in your area. This is the April air filter They were real popular back in the day and It kind of just folds up like that right there It don't look horrible, but I'll tell you this much this pressures and super heat sucked No, I don't know. I'm just gonna change it Can't go from there with it All right, so we went ahead and left it out I talked to the people in charge And I even called some of our guys and asked them about it and they thought we'd removed it when we replaced the unit So somebody probably was used to putting it back in and they just kept doing it and supposedly it was just changed in April So Basically, we're just gonna leave it out. It's killing my super heat All right guys that wraps that one up But just one of those weird oddities how did it last all those years? So I mean in all reality It probably was survived, but I'm not taking the chance. You seen it was wrong. I corrected it. It's better now You know back in the day they used to have smoking in this bar and now they don't so it's not needed The evaporator is perfectly clean. It has two inch filters in there. So they're good to go We got everything taken care of everything's wrapped up. That's the end of the day It's also the end of the video if you guys liked it and you want to see more like it Please give it a thumbs up until next time guys. We'll catch you on the next one